TPH-LBF-IA1.36.DE.0, Fieldbus Surge Protector, Trunk Installation on Power Hub
[ Backorder Available, Ships in 3+ Weeks ]
Fieldbus Surge Protector, Trunk Installation on Power Hub, TPH-LBF-IA1.36.DE.0
|TPH-LBF-IA1.36.DE.0||Fieldbus Surge Protector without diagnosis|
|TPH-LBF-IA1.36.DE.1||Fieldbus Surge Protector with diagnosis|
- Pluggable, mounts between Power Hub and trunk cable
- Intrinsically safe (Ex ia), FISCO, Entity, DART Fieldbus, or general-purpose
- Optional diagnostics for wear
- Grounding of shield direct
- For FOUNDATION Fieldbus H1 and PROFIBUS PA
- Indication via LED and Advanced Diagnostics
This fieldbus surge protector is in accordance with IEC 61158-2 and mounts on the trunk connector of FieldConnex® High-Density and Compact Power Hubs, protecting them. It directs power surges to earth via gas discharge tubes. It is certified intrinsically safe for circuits in hazardous areas up to Zone 0/Div. 1 and DART fieldbus. The surge protector is installed in Zone 1 … 2 or Div. 1 … 2.
Integrated diagnostics (option) continuously monitor wear caused by surges. The end of the useful life and thus the need for exchange is indicated in two ways: via an LED and in the control room via the FieldConnex® Advanced Diagnostics software.
Installation on the trunk connector is without additional wiring even as retrofit. A single grounding bar connects surge protectors mounted side by side to a common grounding point.
We Also Recommend
TPH-LBF-IA1.36.DE.1, Fieldbus Surge Protector, Trunk Installation on Power Hub
0 In Stock